APSP has announced the newly revised ANSI/APSP/ICC-11 2019 Standard for Water Quality in Public...
The Independent Pool and Spa Service Association has expanded its Education Fund and will now...
Last week, New Jersey Governor Phil Murphy signed into law a bill establishing license...
It’s hard to talk about bromine without mentioning chlorine, its main complement in leisure water sanitizing. Bromine is in the same chemical family as chlorine, and functions in much the same way. Bromine, like chlorine, is a sanitizer and oxidizer that destroys organic contaminants in pools and spas.
Bromine dominates spa sanitizing, and chlorine dominates pools, for practical reasons, among them chlorine’s sensitivity to high pH spikes (common in spas) and the fact that chlorine is easier to protect against degradation under the UV rays of the sun. And chlorine is more convenient to apply in pools.
RELATED: Bromine in Swimming Pools?
Bromine can be introduced into water via tablets, granular distribution, as part of a salt/oxidizer system or with an electrolytic bromine generator. But no matter how it is applied, the end goal is the production of hypobromous acid (HOBr) and hypobromite ion (OBr-). The biocidal properties of bromine are primarily due to HOBr.
Even in tablets where chlorine is a component, or in systems that employ sodium bromide and chlorine together, HOBr is still the primary sanitizer present in the water. This occurs since hypochlorous acid (HOCl) readily reacts with bromide ions in solution to make a new molecule of HOBr and a chloride ion (Cl- ).
Bromine will combine with organic contaminants in the water to form combined bromine (bromamines). But unlike combined chlorine, which is a slow-acting sanitizer, bromamines retain their efficient sanitizing properties.
Bromine has a low odor and is effective over a wide pH range. In the recommended pH range for swimming pools of 7.2 to 7.8, HOBr formation remains over 90 percent. At pH of 8.0, HOBr formation is still 83 percent compared to HOCl formation from chlorine at 23 percent. For this reason, in systems where pH may drift upward for short periods of time (i.e., hot tubs and spas) bromine is a popular choice.
Sunlight degrades both HOBr and HOCl. The stabilizer used for chlorine-treated pools (cyanuric acid) is not effective with bromine treated pools. Dimethylhydantoin (DMH), a chemical incorporated into bromine tablets provides some minor protection to HOBr against sunlight degradation.
According to ANSI/APSP/ICC-11 Standard for Water Quality in Public Pools, the ideal range for bromine is 3 to 4 ppm for pools and 4 to 6 for spas. Test kits designed for measuring bromine are widely available. Note that when testing for bromine with a chlorine test kit, the reading should be multiplied by 2.25 to obtain the bromine concentration. Additionally, Oxidation-Reduction Potential (ORP) may be used to test bromine-treated water; however, the reading will be lower than that obtained for chlorine.
Current test kits and test strips will not distinguish between free and combined bromine. Both will test as free. Consequently, while combined chlorine readings in chlorinated pools and spas serve as a reminder of the need for oxidation of contaminants, there is no such indication in brominated pools and spas. The need for oxidation is often overlooked as irritating contaminants, such as brominated disinfection byproducts, accumulate in the water. This could lead to a higher incidence of dermatitis associated with the use of bromine than chlorine.
Once bromine is used in a pool, it will remain a bromine pool, even if bromine is discontinued and chlorine is used. A popular misconception is that the pool must be drained to switch to chlorine. While that is the quickest method of converting a pool to chlorine, a pool with bromine or bromide ions can switch back to a chlorine pool over time. The greater the amount of oxidation and the greater the amount of sunlight present, the shorter that conversion time. Keep in mind that during the conversion process, chlorine demand will remain high.
RELATED: Bromine Generation in Hot Tubs: A Chemistry Primer
Bromine tablets are white solids that are typically sold as compressed tablets or as capsule-shaped briquettes. The most prevalent forms of bromine tablets are 1-bromo-3-chloro-5, 5-dimethylhydantoin (BCDMH) and a tablet composed of a mixture of three chemicals: BCDMH, 1,3-dichloro-5, 5-dimethylhydantoin (DCDMH), and 1,3-dichloro-5-ethyl-5- methylhydantoin (DCEMH).
Bromine tablets are typically fed into the water via either a floater or a bromine feeder. Care should be taken when selecting the appropriate delivery system since the two predominant types of bromine tablets dissolve at different rates. Typically, BCDMH will dissolve more slowly than the blended BCDMH, DCDMH, DCEMH tablets.
When added to water, bromine tablets dissolve and react to produce HOBr, HOCl and dimethylhydantoin (DMH) residue. HOBr becomes the primary sanitizer in this system. As the HOBr reacts and generates bromide ions, in the presence of chlorine and other oxidizers, HOBr will be regenerated as the predominant sanitizer. Thus, even with chlorine present in the bromine tablets, bromine is the predominant sanitizer in the water.
Bromine tablets generally have a pH around 4, therefore, pH adjustment to the water will be necessary to maintain proper water balance. Even though bromine is effective over a wide pH range, it is important that the ANSI/APSP/ICC-11 recommended pH range of 7.2 to 7.8 and alkalinity range of 60 to 180 ppm be maintained.
As with chlorine sanitizers, it is recommended to periodically shock oxidize the water when using bromine tablets. Product label directions should be consulted to identify the type and frequency of supplemental oxidation treatments.
Bromine can be generated on site with a two-part system. The first part is sodium bromide. This typically is introduced as a granular or a liquid solution directly into the pool or spa. The sodium bromide creates bromide ions in the water, often referred to as a “bromide bank.” The sodium bromide alone is not a sanitizer. The second part of the system is an oxidizer, typically potassium monopersulfate, but can also be chlorine. When the oxidizer is added to the water, the bromide ions are oxidized into HOBr which is the active sanitizer in the system.
As the HOBr is used in sanitization, it reduces back into bromide ions which can then be converted back into bromine with additional oxidizer. Sodium bromide only needs to be added periodically to maintain the system.
There are two types of granular bromine. One is bromo-chloro hydantoins similar to those used in bromine tablets. This granular form performs in the same way as the bromine tablets. The second is a mixture of sodium bromide and dichlor (packaged as a single product). This operates in a similar fashion as the two-part bromine systems described above. Granular products are introduced into the pool or spa through manual dispersion onto the water.
Bromine is an effective algaecide, particularly against difficult to control mustard and black algae, and its algaecidal properties are well known. Sodium bromide, as a source of bromine, has been EPA registered as an algaecide. However, sodium bromide alone will not kill algae. To be effective, it must be used in conjunction with an oxidizer, typically chlorine. If using sodium bromide as an algaecide, ensure that the product is EPA registered for that purpose and follow all label directions.
To ensure safe use and handling, all individuals involved in the manufacture, distribution, sale or end-use of bromine must be properly trained and aware of product label sections that address the “Precautionary Statement, Environmental Hazards, and Physical and Chemical Hazards.” A safety data sheet should be read and understood by all individuals involved in the use of these products. Bromine tablets, granular bromine and bromine systems are oxidizers and must be handled properly. Avoid contact between bromine tablets or bromine compounds and easily oxidizable materials such as ammonia, urea, nitrogen-containing compounds, strong reducing agents and other oxidizers regardless of their structure. Never place bromine tablets or compounds in any chemical feeder or floater with any other chemical, including chlorine. Store products in a cool, dry, well-ventilated area away from heat, open flames, organic material, and direct sunlight. Always store in original container and avoid getting the product wet in storage. The use of ozone in conjunction with bromine as a primary sanitizer is not recommended due to the increased formation of the carcinogen bromate.
APSP has announced the newly revised ANSI/APSP/ICC-11 2019 Standard for Water Quality in Public Pools and Spas, which features significant changes that will impact pool and spa service professionals across the nation.
The new Standard is the first comprehensive, data-driven and knowledge-based national Standard for pool and spa water quality and chemistry. It is ideal for understanding the minimum guidelines surrounding water quality parameters in public swimming pools and spas for...
Master Spas Hit the marketing goldmine in early December when television star Steve Harvey gave away five of the company's Michael Phelps Legend Series hot tubs on his syndicated daytime talk show.
Each day during the giveaway, Harvey gave one audience member a chance to play a game called Harvey's Hundreds, a...
The following content is supported by one of our advertising partners. To learn more about sponsored content, click here.
Mechanicsburg is a town in Pennsylvania midway between Philadelphia and Pittsburgh. It’s a bit closer to Philly geographically, but culturally it has more in common with the Steel City to the west. The small borough is home to a pool company called Aquavisions, Incorporated, which...
An industry pro went on Facebook to find a "customer" writing negative comments on her company page — but they were never a customer to begin with! Should she speak up and defend herself or simply keep quiet? Industry pros share their insights:
Paige Pruett-WichernPruett's Pool and Spa | West Plains, Mo.
"What would you do if a 'customer' is publicly posting untrue comments about your company on...